1-1/2" FNPT Stainless Steel Electronic Ball Valve 2-Way
DYNAQUIP CONTROLS| Zoro #: G1573424| Mfr #: E2S27AJE22
Zoro #: G1573424Mfr. Part #: E2S27AJE22
This item ships free. DetailsStandard ground shipping
|Zoro #: G1573424 Mfr #: E2S27AJE22|
|Port: Full||Ball Valve Product Group: Actuated|
|Valve Structure: 2-Piece||Item: Electronic Actuated Ball Valve|
|Voltage: 120VAC||Mount: Direct|
|Standards: NEMA 4, NEMA 4X, ISO5211, ASTM A351-CF8M, ASTM A276-316||Body Style: 2-Way|
|Max. Steam Pressure: 150 PSI WSP||Body Material: 316 Stainless Steel|
|Ball Material: CF8M Stainless Steel||Connection Type: FNPT x FNPT|
|Temp. Range: -4 Degrees to 392 Degrees F||Max. Pressure: 1000 psi CWP|
|Max. Operating Pressure Differential: 300 psi||Stem Material: 316 Stainless Steel|
|Stem Type: Blowout Proof||Seat Material: PTFE|
|Ambient Temp. Range: -40 Degrees to 150 Degrees F||Pipe Size: 1-1/2"|
|Valve Basic Body Material: Stainless Steel||Body Seal Material: PTFE/Viton|
|Country of Origin (subject to change): United States|
Protect against leaks in the system with this electronic actuated ball valve from DynaQuip Controls. This top-of-the-line electronic actuated ball valve is equipped with a 2-piece valve structure. It also has a 2-way body style and a FNPT x FNPT connection. It fits a pipe size of 1-1/2". The ball is made of CF8M Stainless Steel. The temperature range is from -4 degrees to 392 degrees F. It includes a full port. It has a blowout proof stem made of 316 Stainless Steel. The body is made of 316 stainless steel material. The electronic actuated ball valve has a maximum pressure of 1000 psi CWP. It has a voltage of 120VAC. The seat is made of PTFE material. Standards include: NEMA 4, NEMA 4X, ISO5211, ASTM A351-CF8M, ASTM A276-316.
Restrictions and Compliance
- This product has been manufactured to be compliant with the “Safe Drinking Water Act” requirements for low lead in potable (human consumption - drinking and cooking) and non-potable water applications (non-human consumption).
- This is a restricted item in CA, LA, MD, VT. It cannot be used for potable water applications.