1/2" FNPT Stainless Steel Electronic Ball Valve 2-Way
DYNAQUIP CONTROLS| Zoro #: G1880401| Mfr #: E2S23AJE23
Zoro #: G1880401Mfr. Part #: E2S23AJE23
This item ships free. DetailsStandard ground shipping
|Zoro #: G1880401 Mfr #: E2S23AJE23|
|Port: Full||Ball Valve Product Group: Actuated|
|Valve Structure: 2-Piece||Item: Electronic Actuated Ball Valve|
|Voltage: 120VAC||Mount: Direct|
|Standards: NEMA 4, NEMA 4X, ISO5211, ASTM A351-CF8M, ASTM A276-316||Body Seal Material: PTFE/Viton|
|Body Style: 2-Way||Max. Steam Pressure: 150 PSI WSP|
|Body Material: 316 Stainless Steel||Ball Material: CF8M Stainless Steel|
|Connection Type: FNPT x FNPT||Temp. Range: -4 Degrees to 392 Degrees F|
|Max. Pressure: 1000 psi CWP||Max. Operating Pressure Differential: 500 psi|
|Stem Material: 316 Stainless Steel||Stem Type: Blowout Proof|
|Seat Material: PTFE||Ambient Temp. Range: -40 Degrees to 150 Degrees F|
|Pipe Size: 1/2"||Valve Basic Body Material: Stainless Steel|
|Country of Origin (subject to change): United States|
This electronic actuated ball valve from DynaQuip Controls is a reliable shut-off valve for a number of systems. This top-of-the-line electronic actuated ball valve is equipped with a 2-piece valve structure. It also has a 2-way body style and a FNPT x FNPT connection. The temperature range is from -4 degrees to 392 degrees F. The seat is made of PTFE material. It fits a pipe size of 1/2". It has a voltage of 120VAC. It includes a full port. The body is made of 316 stainless steel material. It has a blowout proof stem made of 316 Stainless Steel. The ball is made of CF8M Stainless Steel. The electronic actuated ball valve has a maximum pressure of 1000 psi CWP. Standards include: NEMA 4, NEMA 4X, ISO5211, ASTM A351-CF8M, ASTM A276-316.
Restrictions and Compliance
- This product has been manufactured to be compliant with the “Safe Drinking Water Act” requirements for low lead in potable (human consumption - drinking and cooking) and non-potable water applications (non-human consumption).
- This is a restricted item in CA, LA, MD, VT. It cannot be used for potable water applications.